Solenoid valves Danfoss servo piston operated type EV245B
Kitoma Indonesia - menyediakan Solenoid valves 2/2-ways servo piston operated type EV245B
EV245B is a servo piston operated 2/2-way solenoid valve for use in steam application.
The servo-operated piston design with PTFE seal on the main orifice and steel valve plate in the armature secures a reliable function and long life in steam applications.
- EV245B used with BQ coil, ac voltage up to 185ºC
- EV245B used with BN coil, dc voltage up to 160ºC
- EV245B used with BB coil, ac voltage up to 160ºC or dc voltage up to 140ºC
- Specifically designed for steam applications,
- 160°C or 185°C
- Servo piston operated
- DN 15 - DN 20
- ƒƒAmbient temperature: +40°C
- G 1/2” to G 3/4”
- ƒƒBrass valve body
- NC (normally closed)
||Vertical solenoid system is recommended|
|Max. test pressure||25 bar|
|Time to open||Max. 0.2 s|
|Time to close||Max. 2 s|
|Ambient temperature||Max. 40°C at a medium temperature of 185°C|
|Medium temperature||185°C with ac BQ coil / 160°C with dc BN coil / 140°C with dc BB coil|
||max. 50 cSt|
|Valve body/cover||EN 12165, CW 617N|
|Armature/Armature stop||Stainless steel, W. no. 1.4105 / AISI 430FR|
|Armature tube||Stainless steel, W. no. 1.4306 / AISI 304L|
|Spring||Stainless steel, W. no. 1.4310 / AISI 301|
|Piston ring||PTFE with grafite|
||Stainless steel, W. no. 1.4122|
Coil voltage disconnected (closed):
When the voltage is disconnected, the valve plate (2) is pressed down against the pilot orifice (3) by the armature spring (4). The pressure across the piston (6) is built up via the equalizing orifice (5).
The piston closes the main orifice (7) as soon as the pressure across the piston is equivalent to the inlet pressure. The valve will be closed for as long as the voltage to the coil is disconnected.
Coil voltage connected (open):
When voltage is applied to the coil (1), the pilot orifice (3) is opened. As the pilot orifice is larger than the equalising orifice (5), the pressure across the piston (6) drops and therefore it is lifted clear of the main orifice (7). The valve is now open for unimpeded flow and will be open for as long as the minimum differential pressure across the valve is maintained, and for as long as there is voltage to the coil.
Untuk informasi lebih lanjut silakan hubungi bagian Marketing kami, kami senang untuk membantu :
|Hubungi||: Sales & Marketing
: Simprug Plaza
Jl. Simprug Raya Blok B.2 No.5 Cikarang Baru Jababeka II - Bekasi 17530
||: 021 2851 8058 | 021 2851 8059 | 021 3725 0521 | 021 4448 9918
|Mobile||: 0821 2570 0690 | 0858 9027 2127 | 0877 8228 6338
|Fax||: 021 2851 8058|
|: email@example.com | firstname.lastname@example.org | email@example.com|